There are transmitters installed directly on a liquid service line that is at an inaccessible location. I need to install field indicators, i.e rosemount 751, from these inaccessible flow transmitters to a the decking or ground level on stanchions.
I am considering Identifying the JB and inserting a loop for the field indicator on the ground level via a TB in the JB in series to the transmitter that is at an inaccessible location.
Is there any other feasible solution to this problem?
Sounds good to me, unless the transmitter uses Foundation Fieldbus or Profibus, neither of which use 4-20mA.
In case it is using FOUNDATION fieldbus, you can use the model remote 752 indicator in parallel