Starting a Synchronous Motor
Please help me fully understand exactly how a large synchronous motor is started?
Trip Log Display on Speedtronic Mark 5
We have a problem with the trip log display on our Gas Turbine, equipped with Speedtronic Mark 5 system (RST) and HMI cimplicity 3.22
By DAMENE on 17 April, 2015 - 6:32 pm
Dear Rabhi, Dear CSA Is there a cards to replace on the Speedtronic Mark 5? to resolve this...
By rabhi on 17 April, 2015 - 2:21 am
Hi Damene, Can you provide your e-mail id, i may be able to share some documents with you. ...
Is software of Mark VIe the same as Mark VI?
Turbomach Taurus 60 Gas turbine Speed Deviation Fault
Gas turbine speed deviation fault
Gas Turbine control - Hardware Part Trip of L4
When Hardware causes the trip of L4
Transformer Differential Relay Protection during Open-Phase
Transformer Differential Relay Protection during Open-Phase. Possibility of the relay to trip during line to ground fault or open conductor outside the zone of the differential scheme?
Gas Turbine Efficiency/Power Output vs Relative Humidity and Specific Humidity
Posted by sriramsandeep on 1 April, 2015 - 1:15 pm
gas turbine efficiency/power output vs Relative humidity and Specific humidity
By REI on 8 April, 2015 - 9:42 am
GER3571. Download it in http://site.ge-energy.com/prod_serv/products/tech_docs/en/all_gers.htm ...
DSLC from Woodward Not Operate in Droop?
Does DSLC woodward have restriction operating on droop?
By 309EGuy on 16 April, 2015 - 6:56 am
Terminal 47 is the CB AUX contact. If you open, or have no connection, to the terminal the DSLC...
GE Mark VI/VIe HMI and Software Questions
Specific questions about Mark VI and VIe.
By Jeffery Johnston on 16 April, 2015 - 12:31 pm
Kevin, You seem very proficient in the GE world of turbine controls and i'm a new controls...
Mark-VI VCMI Card Fault Alarm (code: 57,67)
By Rabhi on 16 April, 2015 - 3:25 am
Hi, I would be able to help you and would like to e-mail me the issue with any screenshots. If...
260 kVA Diesel Generator Drops Under 250 A load
260 kVa FGWilson Diesel Genset drops voltage when under 250 amps load
Water Injection System of GE Frame 9e
What rate does water inject into turbine in liquid fuel gas turbine on preselected and BASE LOAD?
Steam Turbine with High Vibration on Main Control Oil Pump
Vibration found high in control oil line and vibration reaches up to 140 micron. vibration is cyclic and suddenly increases
By Anil on 14 April, 2015 - 5:07 am
Dear friend can you plz inform how did the problem get solved and what was the reason?...
Power Factor and Load Angle in Synchronous Generator
The relationship between the inner workings of the generator and the mathematics
Generator ramp rates, prohibited zones and valve point effects
GE Frame 9E MS9001E Air Processing Unit
The working of the Air processing unit APU
By 309eguy on 11 April, 2015 - 7:26 am
This sounds like the bearing 2 breather pipe. You are seeing oil mist. When you had a grid loss the...
Gas Splitter Valve Split and Stroke Out of Mark V?
Difference between premix fuel split set point from 83,25% split (fixed) and gas splitter valve command stroke (78,8...%). Whats happening in the MARK V?
Toolbox EGD Configuration and OPC
Connecting mark vi using Matrikon OPC.
Error when trying to run the GTG.gef in cimplicity HMI.
Does an extremely high demand of power lower the bus voltage on a nationwide grid?
on 8 April, 2015 - 6:03 pm
job2004, If these are rental equipments, then it would seem the supplier would be able to help...