Gas Turbine Generation Not Increasing
Load (MW) is no longer increasing in to original MW.
Why is it not advisable to do welding near Gas Turbine?
Gas Turbine Startup Problem
IGV not opening during startup of Gas Turbine
Gas Turbine Mist eleiminator
Purpose of Mist eliminator in Gas Turbine Lube oil system
GE Gas Turbine Axial Movement
Axial movement of load gear on GE Gas Turbine
On the morning of July 25th we encountered an unfamiliar alarm in our Mark V system for our GE7EA and would like feedback on resolving the issue.
on 31 July, 2015 - 9:44 am
mbaviche, Another thing I'd like to mention is that if this is the first time you've encountered...
on 29 July, 2015 - 3:03 pm
The 'TCCA Status S page xmit failure' alarm refers to the communications link between the Mark V...
How to calibrate the IGV? Frame9E/simple cycle
on 22 July, 2015 - 9:25 pm
Maythem, The Speedtronic community here at control.com has been going strong for over 12 years....
Change the IGV Angle Curve on Mark V HMI
Looking for technical information about effects of changing the IGV angle curve on Mark V HMI
Generator Synchronizing Issue
Generator that was recently rewound (G2) is connected back up. G1 is placed online. G2 is running. Turn G2 sync scope on and moves slowly CCW. Increase speed of G2, sync scope moves fast in CCW direction.
on 30 July, 2015 - 4:20 pm
Jim, When the speed of G2 was increased, what did the governor say happened to the prime mover...
When to Use Industrial Motor Frame Grounding
Lazy electrician doesn't want to connect motor frame grounds in a power plant. Claims NEC rules don't apply. Whose rules do?
By Valen on 30 July, 2015 - 5:15 am
Dear Phil, Thank you very much for you invaluable help and interest. Best regards...
Turbine Generator Offline and On Turning Gear
Looking for answer to recent test question
Condenser Vacuum Levels Rising
Vacuum level rising above normal levels especially during start up
GE 9E DLN1 secondary flame trouble
Secondary flame needs so long time to be stable (up to one hour )
GT CCR HMI is not showing alarms in alarm viewer or cimplicity screen.
By CuriousOne on 27 July, 2015 - 8:38 pm
This is nothing new with alarm manager snap-in. You must re-establish the connection within alarm...
High Vibration in Pump Drive End Bearing
Higher vibration in Pump Driving end bearing about 80 micron is observed in all three pumps (TDBFP-A, B and MDBFP)
7EA-Dual Fuel--Liquid Fuel Purge 20PL-4 Valve
Can some explain the functionality of the 7EA-Dual Fuel--Liquid Fuel purge 20PL-4 valve?
Gas Turbine Tripped on Fire Detectors
GT tripped on UV fire detectors 2 on accessory compartment, there is no fire, what could be the cause??
By Bob Johnston on 25 July, 2015 - 7:27 pm
Many things can trip UV detectors, sunlight, welding nearby, halogen lamps/torches....
on 25 July, 2015 - 3:05 pm
Sundar2015, Either there's a wiring error, or the sensors detected smoke, UV and/or temperature...
GE Frame 6 Gas Turbine bleed air valves
15 MW Generator in Island Mode Trips on Dead Machine Protection
15 MW STG tripping on dead machine protection while running in island mode
GE Frame 5 tripped when full load 18MW, premix mode.
Advice on What an Power Plant Electrical Maintenance Engineer Be Doing
What Should Electrical Maintenance Engineer Be Doing To Distinguish himself?
Cimplicity 6.1 License Issue
Cimplicity 6.1 licensing and windows compatibility
By Russ B. on 21 July, 2015 - 9:21 am
GE Fanuc is GE Intelligent Platforms. You should contact your local rep or agent to get details on...
Failure to Reignite Primary Zone
facing problem in re igniting the primary zone while shutting down