DORIC Temperature Indicator
Posted by sultan Khan on 17 May, 2018 - 11:16 am
DORIC digital temperature indicator used in Mk 2 panel does not indicate any temperature value, but only flickers. It is a mv to temp. converter for "K" type thermocouple.
By sultan khan on 20 May, 2018 - 11:39 am
Hi.. You have not given your particulars or contact details... >I have one new Doric if...
By sultan khan on 19 May, 2018 - 12:01 pm
Hi, Mr.David. No one knows about Order code but requirement was for use with K type TC and input...
By sultan khan on 18 May, 2018 - 12:53 pm
Mr. David.. Thanks a lot for your kind response. the meter was ordered by some one long back....
Gas Turbine Control and Efficiency
Gas turbine temperature control system and efficiency
on 20 May, 2018 - 10:16 am
surya, For a machine of that vintage (age) with conventional combustors and operating in simple...
on 19 May, 2018 - 11:53 am
surya, Also, does the turbine you look for exhaust to atmosphere (simple cycle), or into an HRSG...
Different CPDs for similar frame6B machine at same loads
on 18 May, 2018 - 4:05 pm
It's atypical for a machine with DLN-I combustors to have only a single CPD transmitter since CPD...
Steam Turbine Control Oil Pressure Dip
Have sudden pressure dip in control oil pressure from 180 bar to 140 bar for 60MW GE steam turbine
on 18 May, 2018 - 12:48 pm
There is no doubt the pressure drop is real; it's the cause that is in doubt. I'm not familiar...
on 8 May, 2018 - 3:16 pm
mabdullahkhan, If it's not always the same pump, then I would be looking for something that is...
By mabdullahkhan on 8 May, 2018 - 7:56 am
>Is it always the same pump which experiences the drop in pressure? Response: No it is not...
Problems with replace to VCMIH2B card for VCMIH2C card.
MARK 2 Temperature Averaging
Posted by sultan khan on 12 May, 2018 - 12:24 pm
Mk2 speedtronic Temperature Averaging Module problem.
By sultan khan on 17 May, 2018 - 10:12 am
>OK. Are you sure that the SCZA card in slot "D" of the >calibrator is working?...
By sultan khan on 14 May, 2018 - 11:08 am
Thank you sir, for your quick response. You are very correct in your statement,sir. When we reject...
significance of forceback attribute in maxDNA.
By Supratim Pal on 17 May, 2018 - 2:30 am
ForceBack is going to help you if you want to force the PID to some value in Auto Mode, value may...
Power Generator Reactive Power Consumption
Power generator reactive power generating vs. taking in
Issues with Power Generation when in Sync with the Utility Supply
Issues with the power generated when in sync with the Utility supply.
on 15 May, 2018 - 1:21 pm
Nick, What happens when a synchronous generator is synchronized to a (very very) stable grid is...
on 14 May, 2018 - 1:41 am
Hi Gentlemen I have been extremely impressed by what you have returned here. There are similar...
What Is Your Fuel Valve Performance for This Case?
Time of starting load for gas turbine when synchronize with national grid
Gas turbine went to NO STATUS during mode change over.
Single Core Drop During Gas Valve Manual Movement
While attempting to manually move gas valves on a Mark V controlled 7EA Combustion Turbine a single core drops out registering a speed increased more than 5%. Problem happens intermittently, cause unknown.
on 9 May, 2018 - 5:51 pm
anon, >Years ago, I had a recommendation to short the UNUSED (LP) >Speed inputs during...
By anon on 9 May, 2018 - 3:02 pm
Years ago, I had a recommendation to short the UNUSED (LP) Speed inputs during autocal if this...
Sample P&ID for an air cooled condenser
MARK VIe-ToolBoxST Modules
Posted by Rasheed on 3 May, 2018 - 5:19 am
Toolbox ST Modules help Module M7FA051A1011_1
on 9 May, 2018 - 5:28 pm
Rasheed, So, I just had occasion to see a ToolboxST file for a 7FA.05, and I checked the MBC...
on 9 May, 2018 - 10:24 am
Rasheed, GE seems to be producing fewer and fewer help descriptions for their blocks. Don't...
By Rasheed on 9 May, 2018 - 4:45 am
Thanks for the response. Yes that's correct. I am referring to the block & block help is...
IGV Actuator Span in DGA too big
GE Frame 6B Actuator replacement. Gross stroke 38mm however IGV blades travel more than 60DGA.
on 8 May, 2018 - 1:54 pm
Frame6BNewB, As long as the IGVs can travel between 34- and 86 DGA without hitting a stop...
Fr9E Exhaust Temperature Controlling Curves
Understand different exhaust temperature control parameters/ Limits
on 9 May, 2018 - 11:34 am
novice001, Mark* turbine control systems use a MIMIMUM SELECT function to choose which scheme is...
Installation of Toolbox st v7.0
Having difficulty during installation of toolbox st v7.0
Gas Turbine FR9E High Exhaust Pressure
Gas Turbine GE Frame 9E in combined cycle operation is experiencing high exhaust pressure reaching 15Kpa.
Frame-V Machine with AA Cooler CW Bypassed
Can AA cooler CW be stopped for 30 min? what are the risks?
on 8 May, 2018 - 4:07 pm
barindra75, Sorry for not catching the spell checker/corrector mistake on your name on my...