Self Cleaning Inlet Air Filters Puffing Air Temperature
Can we clean/puff the turbine inlet air filters with an air of temperature up to 80degC-90degC?
Replacing Gas Turbine Lube Oil
Procedure for replacing the gas turbine complete lube oil
Instantaneous Current Flowing Through a Line
What will be the instantaneous current flowing through the line?
Correct method for changing SDCC card
Basic Instrumentation in 6FA with MARK V
Need guidance to understand a 6FA With MARK V system in better way
MARK VIe Controller Replacement
Replacing MARK VIe UCSBH1A controller
By vkg on 14 January, 2018 - 11:56 am
I need procedure of controller UCSB replacement. I have seen in document but it was available of...
By chirus on 9 January, 2018 - 9:36 am
mhwest, Can u please provide the procedure to the below mail? Chiranjeevi.Sornapudi@hpcl.in...
Formula to Calculate TTXM in 9E Gas Turbine
What is the formula to calculate TTXM in 9E gas turbine for MARK Vie?
GE 6FA Gas Turbine Shutdown
Gas Turbine 8 minutes holding at 90% rpm once stop command given after reached FSNL.
Calculating the Fuel Consumption Efficiency of a Gas Turbine
How to calculate the fuel consumption efficiency of a GE gas turbine?
Mark Vie Diagnostic Alarm Disable
How to disable unused diagnostic alarms?
Gas turbine tripped with L12 HFD_P HP OVERSPEED FAULT PROTECTION SPEED INPUT TRBL
By djafer on 7 January, 2018 - 7:22 am
Many thanks CSA and mfrasca12, really I have appreciated your support and help. I make report,...
By Djafer on 3 January, 2018 - 12:37 am
Dear CSA; Many thanks for your response, really we appreciate your support. - I have checked...
Incorrenct Flow Measurement in the Outlet of Feed Water Pump
Flow measurement 0 values in control valve openings lower than 30%
By d on 2 January, 2018 - 2:24 pm
30% flow and less translates into 9% and less of the d/p xmtr span. typically, you generally...
Controlling PMS with Fuzzy Logic
Posted by Ebrahim Golidari on 30 December, 2017 - 3:43 am
Looking for information on how to control a Power Management System using fuzzy logic
Turbine steam flow shows low
By Vijay Yadav on 30 December, 2017 - 2:12 am
Your design reference should be closer to actual. i.e. if you're working pressure is 45 kg/cm2,...
GE Mark VI S Controller Failure
GE Mark VI controller S status offline several days after startup
By Alaqeel on 27 December, 2017 - 7:40 pm
Good day For us we have the problem with rack T. Unfortunately, we replaced VCMI, VPRO and TB...
By Alaqeel on 25 December, 2017 - 3:43 pm
greetings all we faced the almost the same problem Alarm on VPRO Z and VCMI T. we replaced...