Calculation process of FSRT in Mark IV
What is the formula for FSRT calculation in MARK IV?
Gas turbine MS5002B (with Mark VIe control) frequently works in control temperature mode.
By Leandro Carletti on 24 July, 2017 - 9:09 am
working in temperature control for a MS5002 is not abnormal condition. is not a alarm condition is...
By mohamed31 on 19 July, 2017 - 2:24 am
yes I am thankful and this is my email; firstname.lastname@example.org > Send me an email address,...
By mohamed31 on 18 July, 2017 - 3:00 am
yes of course I will be so thankful sending me some valuable documents MS5002B And MARK6e control ...
By mohamed31 on 17 July, 2017 - 9:46 am
thanks for this clarification . first of all THE trips are generally customer trip (process). in...
High Inlet Air Filter Differential Pressure During Rain
Frame 6B machine inlet air filters differential pressure increases significantly during rainy season causing trip.
By senouci sadek on 23 July, 2017 - 3:06 pm
Hi- kh000, My idea is only as proposal to mitigate the impact of high humidity in you...
Looking for a copy of the Yorkshire F6 HV Switchgear manual
Relationship between fuel control and excitation control
By Muhammad Junaid on 21 July, 2017 - 11:21 pm
Great Work.. Superb.. I'm new at 9HA.01 GTG and understood very easily with such...
7500 series combined SRV/GCV assembled together vertically. GCV stem was stuck after recent overhaul.
Unit Trip After 28VDC Loss on MKVIE
Why we're tripped after a failure of 28 vdc power supply network, due to a PDOA fail.
By Seeker on 20 July, 2017 - 11:22 am
Hi Chemsoud, Do you have a spare PDOA? Did you check if the PSVO is working fine?...
Turbine Bearings Sealing Air Supply Transfer Valve (VA-14)
The function of VA14, Turbine bearings sealing air supply transfer valve in Frame 9e
IS215UCVEH2A Battery Discharging
Mark VI IS215UCVEH2A battery is discharging
GE Gas Turbine Thermal Insulation
Lifetime of Rotor at Gas Turbine
What is the lifetime of rotor at gas turbine type BBC-GT9 in EOH?
Exhaust Temp Spread Trip after Selecting IGV Temp Match
The GT trips on high exhaust temperature spread after selecting IGV Temp Matching (transfer from SC into CC)
125VDC Both Legs Having Difference
Mark-Vie 125VDC Input supply -VE phase showing -80VDC and + phase showing +45VDC.
By LFord on 17 July, 2017 - 6:27 pm
I just wanted to thank you for the extremely detailed responses. We are having issues with...
How variastor works in MARK VIe system
By Chiranjeevi on 16 July, 2017 - 11:21 pm
CSA, For analog inputs also it seems MOV is only used. how it protects the currents?...
High Vibration on Bearing
GE unit GT13E2 has high vibration on Bearing No. 1
GE Gas Turbine Major Inspection (MI) Scope
How to optimize the scope of Major Inspection of Industrial Gas Turbines.
Welding the Split-Line of GT Wrapper Casing
The effect of welding the split-line of GT wrapper casing
if two adjacent TTXD fail then will the machine trip?
LM6000 looses power while opening VBV valve
Battery Inside the MARK VIe System
Posted by Chiranjeevi on 13 July, 2017 - 11:05 am
Why are there no batteries inside the MARK VIe system controller?
Diesel Engines Performance
Diesel Engines Performance
Small Gas Flow Explosion Proof Sampling Pump
Looking for a small gas flow explosion proof sampling pump
Control Oil and Hydraulic Oil in Gas Turbines
Difference between control oil and hydraulic oil in gas turbine
Creating a record of signals that records MarkVie trends that lead to a trip.
Main Hydraulic Oil Pressure Surge Observed with IGV LVDT Trouble
GE make frame-V gas turbine. Main hydraulic oil pressure fluctuation observed along with IGV LVDT feedback trouble.
on 10 July, 2017 - 2:08 pm
barindra75, So, first thing to know is most GE-design Frame 5 heavy duty gas turbines don't have...