We operate a baseloaded steam turbine. Lately we have been experiencing load control swings when our AVR is in Automatic. We find ourselves placing the AVR in manual until the load settles out and then restoring back to automatic mode. We have been sending trends to our OEM for months with no identification as to why this is happening, the causes or solutions. We are replacing our AVR's in 6 weeks and am hoping this resolves the issue. Is there anything else we should be looking at?