The problem I am facing is that using the standard configuration the PV550 is showing error "No active nodes found on network", now I have by passed the link coupler and connected the PV550 directly using the 1747-C10 cable from the PLC. In doing this I had to change the PV550 position from its original.Has your SLC500 series PLC a DH-485 connection?
Has your Panelview 550 a DH-485 connection?
If yes to both - where would you wire the screens ?
and the spare cores ?
What’s the length of cable and would it be in an industrial environment ?
Screened 2 core (twisted pair) or preferably armoured with drain wire is appropriate here, and cheaper than CAT 5.
It’s unclear what the link coupler would achieve apart from isolation.
|Thread starter||Similar threads||Forum||Replies||Date|
|S||Can I get the Communication cable Pin details of MESSUNG PLC.||General Automation Chat||1|
|Communication CABLE||General Communications Chat||1|
|K||Frequency Drive and Communication Cable Ground||General Automation Chat||0|
|V||communication cable fpr Omron to Siemens||Programmable Logic Controller - PLC||2|
|A||modbus communication cable||Modbus||2|
by Seth Price