End field device output module accepts 0-27648 as range to give output 4-20mA . Can you guide how this range can be scaled by using SCL function in PLC program?you can use SCL instruction, but the scaling will be depend on your Analog Output module scale.
InEUMax will be the same as your analog output min value at 20 mA and InEUMax will be the same as your analog output min value at 4 mA, InRawMax will be the same as the value that intended to be 20 mA and InRawMin will be the same as the value that intended to be 4 mA
|Thread starter||Similar threads||Forum||Replies||Date|
|H||Mettler Tolledo scale vs other scales from the communication point of view.||Instrumentation & Measurement||0|
|J||help needed with scale RS485 communication||General Communications Chat||18|
|H||PLC and Weight Scale Communication||Programmable Logic Controller - PLC||0|
|C||PR Scale for Magnetic Pick-ups of Flow Divider and Shaft Speed||Power Generation||1|
|L||Analog block scale for S7-300||Computing||0|