33KV/11KV, 15MVA, ONAN cooling.Deji...
Please note, it starts with several relatively simple tests to detect if the Xfmr was unintentionally damaged during the time it was de-energized to the day it's to be re-energized !
If those tests lead to "NO !" Then energize and load it !
BTW, can you provide some info as to Voltage, kVA, Air/Oil cooling, and if equipped with cooling fans !
|Thread starter||Similar threads||Forum||Replies||Date|
|fisher pcv installed in petrol road loading line||Instrumentation & Measurement||12|
|H||Drop in control oil to 55 PSI, and Nozzle goes to current suicide during loading||General Automation Chat||8|
|P||Appium Inspector not loading||Open Control||0|
|Frame 5 GT loading problem after MI||Power Generation||30|
|M||Frame 6 DLN Loading Issue||Power Generation||1|
by Aline Dias
by Gunner Scott