Original poster even gave a quick reply update... So bye byeWith RS-422 four wire you can only connect 2 devices to each other. So there is never a need to set an address - you always know whom you are talking to (= the other).
Now it could be that the vendor says "RS-422 four wire" but actually means: RS-485 four wire. In this case, the device being the master also doesn't need an address. Like in Modbus.
BTW, with RS-485 the normal max device limit per cable segment is 32. You need repeaters to reach 88.
|Thread starter||Similar threads||Forum||Replies||Date|
|M||Siemens PLC Step7 SFC20 & FC10 with Programming error, need help!||Programmable Logic Controller - PLC||4|
|T||Need help with Denkovi Wi-Fi 16 Relay Board PCB - ModBus TCP||Modbus||11|
|M||What do I need to connect a 1500 Micrologix on a DH+||General Communications Chat||1|
|J||Need to connect to Honewell Scan 3000 HMI||Human Machine Interface - HMI||0|
|M||What do I need to connect to a SLC5/05?||Programmable Logic Controller - PLC||10|