Original poster seems not replying... Doing some efforts for no reply can be like pouring water on sands...Use 1 pump in and 1 pump out, both run by VFDs. Control the VFDs with PID loops. You should be able to keep the level fairly stable that way.
|Thread starter||Similar threads||Forum||Replies||Date|
|D||Is Droop Setting Fixed for Frame 5 GE Turbine When Machine Is Designed?||Power Generation||2|
|A||pre loop and loop checking||Process Control||3|
|E||Adding signal names to pre-vote display||Power Generation||0|
|D||Numa-logic PLC timer pre-set||Programmable Logic Controller - PLC||1|
|S||Petrocount transmitter pre amp||Sensors & Calibration||1|
by Seth Price