Today is...
Sunday, August 19, 2018
Welcome to Control.com, the global online
community of automation professionals.
Featured Video...
A demonstration of EtherCAT control of linear motors using the CTC EtherCAT master.
Help keep our servers running...
Flow calculation
Formula for Square root extraction for doing in PLC for flow measurement.

Please let me know the formula for Square root extraction for doing in PLC for flow measurement.

Flow range: 0 -928 m3/hr
Calibration range: 0 - 2500 mmwc

Sumit,

There is a simple formula that could work for the calculation of flow in your situation.

Q=K(SQRT(Hw))

K is a proportionality constant that will take into (during the original design) the effects of units, temperature, expansion factors, density, etc.

If the original data has changed significantly the formula may not work.

You use the original design capacity of what (Q) and (Hw) is at maximum flow then calculate K.

K=Q/(SQRT(Hw))

Once you have K the process is quite easy to calculate (SQRT(Hw)) -- providing your PLC can accomidate the function ((X/Y)^(Z)).

Set Y to 1

Set X to the value of Hw

Set Z to 0.5

Then calculate the flow using Q=K(SQRT(Hw)).

Dennis

By Gopal Krishan on 26 June, 2007 - 5:19 pm

Hello Sumit,

The simple formula for flow calculation is
= Transmitter range in eng unit x Sqrt (Diffrential pressure Field I/P in mmWC/DP range in mmWC).