MKIV R, S, T Communication Link Inoperative
GE frame6b Speedtronic drive by MKIV. In two machines suddenly happen <R>, <S>, <T> communication link inoperative in same time.
Yokogawa Virtual Test Function Error
Been using a CS3000 to run a simulator and started getting a virtual test function locked error
Panel View Plus 1000 Communication
HMI is not browsing with PC
Mark Vie OPC DA Server error
Transmitters Calibration Interval
What is the recommended interval for calibration of transmitters, DP, temperature, and pressure transmitters.
Tags from Unity Pro to CITECT
Export tags from Unity Pro PLC to Vijeo Citect explorer SCADA...
Intouch LGH File to CSV File
Convert .lgh files generated by Wonderware InTouch to .CSV
By Bill_SS on 8 August, 2016 - 12:44 pm
XLReporter, which has been used in industry since 2001, converts LGH files to csv and Excel as...
By Dan on 7 August, 2016 - 8:21 am
You should take a look at LGH File Inspector by WorkSmart Automation. It reads Wonderware LGH...
HINET Modbus DDE SERVER 2014
HINET ModBus DDE SERVER 2014,
By Dave Hunt on 12 September, 2016 - 4:31 pm
I will be testing your DDE server with our FIN Data Collection server which still uses good ole...
Vijeo Citect 7.1 SCADA and Schneider Unity Pro PLC question...
The I-7567 is a USB to HART Converter
Sending data from SCADA to LabView using HART protocol
By Jonas Berge on 8 September, 2016 - 11:56 pm
Use an OPC server for HART. I think LabView supports OPC. Please check. Learn more about OPC...
Zeroed Starts Counters and Total Fired Time Mark V
Trying to understand why starts counters and Total Fired Time Mark V zeroed out.
By mhwest on 8 August, 2016 - 9:31 pm
CSA, It is UNTRUE that the only way to change counters is by PAC case to GE. There is a...
Generator Lockout Relay 86G Won't Reset.
The 86G Reset knob on GCPP won't reset even when there is no standing alarm indicator.
ALSTOM Flakt Bus to Modbus HELP
Need some help, does anyone know Flakt bus? is there any gateway or converter to Modbus or any other protocol?
By Rakesh on 2 September, 2016 - 8:07 am
Hi Martin, Flakt Bus- this topic to new to me. can you share more details? FYI, we are working...
Presentation on MARK VIe...
Looking for a presentation on MARK VIe for plant operators.
Gas Turbine Flowmeter Calibration
Gas Turbine Frame 6B - Honeywell SMV3000 Smart Transmitter, Model SMA 125 Flowmeter Hardware and software calibration
Remote GT Operation Modbus or Ethernet or Controlnet
Is there any limitation /standard/best practice for using Modbus for controlling GT from DCS or remote station??
How to Change Signal Name in SpeedTronic Mark IV
Changing signal name in Gas Turbine control Speedtronic Mark IV
Comparison of various SCADA packages
Posted by Sachin Mane on 5 June, 2001 - 11:22 am
Can anybody explain me the features of various SCADA packages available in industries?
By Bob Peterson on 28 July, 2016 - 12:50 am
You would have to get pricing from a distributor of the product. I suspect it varies from place to...
By Jeremy Pollard on 22 July, 2016 - 4:05 pm
Strongly recommend checking into inductive automation... I wrote a review some time ago... ...
By Prasenjit on 22 July, 2016 - 12:19 am
Dear Bob, Thanks for the reply. Can you give me some information on the licensing part and how...
Is it possible to use RDL or RDLC report files in SCADA?
By Dave Ferguson on 27 July, 2016 - 6:30 pm
I have done work with Rockwell HMI and SSRS, we launch a web browser that calls the report from SQL...
Edit <I> Screens on PC without idos
View and edit screens used on the old <I>'s running idos on my laptop, which can not run idos.
FREE AB DF1 Serial Slave Simulator
Today we released a FREE AB DF1 serial slave simulator.
PM9C Power Meter MODBUS Communication
Posted by Kevin Hella on 15 March, 2016 - 5:27 am
Setting up MODBUS communication between PM9C Schneider power meter and a PLC.
By Kevin Hella on 22 July, 2016 - 2:14 am
Hi David, Just seen your response very late. Actually you gave all the answers. PM9C signal...
Mark VI IONet N-Tron Network switch failures
Mark VI IONet N-Tron Network switches keep on failing, RCA needed
By Badr on 21 July, 2016 - 9:39 am
Hello all, GE sent us a feedback few days ago, they said that the issue of N-tron switches bad...
Siemens HMI to Emerson Drive via Modbus RTU Communication
Convert Decimal to Integer
How can i convert decimal type (0-100) to integer (0-32768)?
Tracing Communication Errors in a Modbus Concentrator
Best practice to show a communication error in a Concentrator to a Scada/HMI using Modbus
By Harvard07 on 19 July, 2016 - 6:58 pm
If you can map a register to a clock second counter (or any counter), your master could then...