My GE gas turbine unit is going to be under AGC control which means that setpoints (4-20ma) are coming from grid control center to my unit every 4 seconds.
My question is that AGC doesn't know about some unit conditions like fuel pressure, thermocouple temperature, some special vibration of unit and which I consider when I assign new setpoint locally to my unit. I mean I check every conditions before assign new setpoints to the unit but AGC doesn't.
So is there any risk for unit trip under AGC control?
If this is a GE-design Frame 9E (or Frame 9EA) heavy duty gas turbine with a Mark* turbine control system and DLN-I (Dry Low NOx 1) combustion system, then, Yes. There are things which the grid company/operator should be (but usually AREN'T) aware of when operating the unit using AGC.
If the gas turbine has conventional (diffusion flame) combustors, then, no; there really isn't anything the grid company/operator really needs to be aware of.
Generally, in a combined cycle power plant the steam turbine is considered a "follower" turbine. That means the power produced by the steam turbine is a function of the gas turbine exhaust temperature and exhaust flow-rate. Even if there are auxiliary (or "duct") burners in the HRSG producing the steam using gas turbine exhaust for the steam turbine there usually isn't any real "control" of the steam turbine load once the plant is on-line. If the GT load (and exhaust temperature and -flow-rate) change, then usually the ST load will also change. (Most combined cycle steam turbines get to a certain load/operating point after the generator breaker has closed, and then the steam turbine control valves go fully ("wide") open--and whatever steam is available from the HRSG is converted to power. So, usually, the grid company/operator doesn't have control of the steam turbine via AGC. They probably have a load signal from the ST and the GT and they just have to be aware that when they change the GT load the ST load will most likely also change. And, they have to adjust the GT load to make the total plant output (GT plus ST) equal to whatever they want the total plant output to be.
We are glad you found this site, and it's very common for newcomers to ask a LOT of questions. The GE-design heavy duty gas turbine control community has been very active here for more than 15 years--so, you should be able to imagine that just about every question has been asked, and answered, at least once before. Perhaps not exactly the question you have, but, one very similar.
There is a 'Search' field very cleverly hidden at the far right of the Menu bar of every desktop version page of control.com. While the search syntax isn't like your favourite World Wide Web browser it is VERY fast and very powerful. And it can be used to search the Archives of control.com for past threads, just using one or more words or terms. It is HIGHLY recommended that you use the Search 'Help' the first couple of time you use Search to get familiar with the syntax of terms and words and modifiers to get the most benefit from searching the control.com Archives.
There is a LOT of information in the Archives, and one of the things that sets control.com apart from many other similar Web-based forums is that when an answer or help is given by someone the person requesting the answer or help writes back to give feedback about the answer or the help. This does two things; first, it lets others know who read the threads (now and in the future) if the information provided was helpful or not. And, second, it lets the person(s) providing the information know if the information was helpful or not. Anyone providing any responses to threads on control.com gets paid EXACTLY the same amount you paid to post your question(s) here on control.com. That is: zero (dollars; gazoonies; pesos; dirhams; RMB; yen; whatever currency). So, by providing feedback original posters let others--and the responders--know if the information provided was helpful (or not, as the case may be). This is good for others, because they know if the information can be used to help resolve their issue(s). And, it's good for the responders because they get some satisfaction from doing a good job, or they can learn from other's experiences and possibly even improve the quality of their future responses. So, it's a win-win for everyone--IF people will just take a couple of minutes and provide feedback about the responses which were offered to their post(s).
Welcome to control.com! (And, remember, it's pretty unlikely your question (present or future) hasn't already been asked or answered in some form or manner. And, by reading past threads in the Archives, you will likely also learn something (many things, hopefully!).)
One thing, though. This site doesn't use avatars. (Avatars are a method for you to post some information about yourself, your experience and knowledge, and the equipment at your site, so that others who might be curious about you or the equipment at your site, can quickly refer to the avatar when posting responses.) So, at least in the beginning, you need to post (and re-post, and possibly re-re-post) some pertinent information about the equipment at your site, any troubleshooting you may have done when posting a problem--AND, most importantly, what the results of your troubleshooting were!. It will help a lot in getting more concise answers to your questions and queries.