Thanks for the reply. I have contacted Daikin, who then contacted there overseas dept. Still waiting 3 weeks later. So I thought I would try this forum. No software installed it's just Modbus, 16bit Interger, just want to know the feedback value expected for heat, cool and fan. It must really be rocket science.Not come across these, but suspect you have asked the card manufacturer (hardware)
how the software performs.
You need to contact Daikin who would more likely have installed their software.
Ah well, worth a try on the forum. When we commission it will be a case of Modscanning and see what we get back and modding software on the fly. I like to get it done before going to site but hey ho.16 bit integers, Modbus protocol and no Software ?!
Not rocket science or pure magic... not so much being economic with the truth - just a manufacture metaphorically holding their cards close to the chest. Nothing personal.
|Thread starter||Similar threads||Forum||Replies||Date|
|P||Communicate with Modbus RTU to EATON IQ100 power meter through Internet||Modbus||3|
|C||Modbus TCP/IP on Ethernet Cable Maximum Distance||Modbus||1|
|D||Intelligent Modbus Gateway Required||General Automation Chat||2|
|L||Question : How I Send AO for a Setpoint Temperature With Modbus RTU||Modbus||2|
|Difference in value on slave and master in Modbus over RS485||Modbus||2|
|Communicate with Modbus RTU to EATON IQ100 power meter through Internet|
|Modbus TCP/IP on Ethernet Cable Maximum Distance|
|Intelligent Modbus Gateway Required|
|Question : How I Send AO for a Setpoint Temperature With Modbus RTU|
|Difference in value on slave and master in Modbus over RS485|