i have 7 plc & only two of them are in up state & the other are in recovery & i couldn't find the reason. i think may be is related to profibus parameters. but i need any new suggestion.
|Thread starter||Similar threads||Forum||Replies||Date|
|D||When to use profibus over Fieldbus||Modbus||3|
|T||Profibus Pa Configuration||Instrumentation & Measurement||4|
|O||Regarding Applicom Profibus and FMS protocol .||Human Machine Interface - HMI||1|
|S||Profibus||General Automation Chat||0|
|G||Profibus Comm Between S7 300 and Emerson Delta V Controller||Networking||6|